G3430 5545 230
Relay load: 16A
Module load: 32A (16 A per relay)
Galvanically separated SPST relay outputs
For mounting on DIN-rail (EN 50022)
LED-indications for supply, Dupline
® carrier and outputs
AC power supply
Address coding by GAP 1605 Mode of Operation 8-channel receiver with 8
normally open contact outputs. Each output is coded by means of the code programmer
GAP 1605. For changing the default setting, please refer to the datasheet on GAP 1605.
The outputs are normally OFF. When a transmitter coded to the selected channel
is activated, the output turns ON and remains ON until the respective channel
The default setting is such that upon loss of Dupline® carrier all the outputs go OFF.
At delivery some of the relays might be ON due to transportation bumps. To be
sure that the relays are OFF, connect the module to power and Dupline and transmit on
channels A1-8 once.
Due to the construction with bistable relays, the module is intended for heating
and light control only.
BH8-CTRLZ – G3800xx01x